To avoid puncturing PEX tubing, use a skilled, careful concrete crew that’s familiar with pouring slabs over PEX circuits. If you detect a leak, you can fix it with a repair coupling or replace the circuit altogether.
How Do You Prevent Puncturing PEX Piping?
If you notice a drop of more than 5 PSI, there’s a leak somewhere in the circuit. If this happens, fix the damage section with either a repair coupling or a replacement circuit, and run the pressure test again.
If the initial pressure test is successful (no more than a 5 PSI drop), go ahead and lower the pressure to 25 PSI, while monitoring the pressure gauge for fluctuations. Now, your crews can finish the final preparations for getting ready for the slab pour.
How Do You Fix a Punctured PEX Tube AFTER a Concrete Pour?
After the concrete pour, you can fix a punctured section of PEX tube using the 4 steps below.
- Remove anywhere between 4 and 8 inches of concrete around the puncture.
- Cut out about ½-inch or the damaged tubing and reconnect the ends with a repair coupling.
- Protect the coupling with self-fusing tape, aka fire tape or self-vulcanizing tape.
- Place fresh concrete back into the opening. That’s it — you’re done!
Though repairing a punctured PEX tube may seem like an arduous task, it’s actually not — as long as you stick to the steps above!
Don't miss a thing!
Subscribe for exclusive content, insider industry news and limited edition webcasts.
Best Practices For Designing and Installing Hydronic Radiant Floor Heating
If you install hydronic radiant floors in the homes you build, you know you only have one shot to get the job done right —
How Heat-Sheet® Heavy Works As An Effective Under-Slab Radon Mitigation Insulation Layer
You may know Heat-Sheet® as a convenient solution for installing PEX tubes in hydronic radiant floors. But did you know that Heat-Sheet® also makes for
The Future of Hydronic Heated Floors Amidst A Shift Away From Fossil Fuels (And Why They’re Still Worth It)
As fewer customers consider fossil fuels to be a desirable long term heating option, you may be asking yourself: should I still install hydronically heated